Appendix A – M24 Fluokit Disposal Procedures. Fluokit Indoor Ring Main Units contain Sulphur Hexafluoride (SF6) gas as an insulating medium which is. AIR INSULATED SWITCHGEAR. FLUOKIT M+ MV modular switchgear up to 24kV. Technical Specifications. AREVA T&D. Summary. Cubicle equipment. FLUOKIT M+ cubicles include the following features: Operating Cubicles in the FLUOKIT M+ range all have functional . Fluokit M24 & M24+ meets your.
|Published (Last):||9 October 2006|
|PDF File Size:||12.84 Mb|
|ePub File Size:||6.2 Mb|
|Price:||Free* [*Free Regsitration Required]|
This user manual does not list the locking-out procedures that must be applied.
Local safety requirements which ffluokit in accordance with these instructions, especially those regarding the safety of product operators and other site workers, must be observed.
Cable troughs and ducts must be blocked up to avoid: The delimitation of the civil engineering layout depends on the type and quantity of materials to be installed refer to the following chapters.
They must be in the same horizontal plane. The average water vapour pressure over a period of 24 hours must not exceed 22 mbar. Certain passages must be sufficient for free movement and execution of operation and maintenance manoeuvres, – leave the room’s access door free, – take all measures to prevent all incidence of climatic conditions humidity, pollution, etc. Layout on a type 2 cable trough, with width of more than 50cm Whenever the width of the cable trough exceeds 50 cm, it is necessary to fit the longitudinal support irons to support the left and right-hand uprights for each Functional Unit.
Complete this assembly by the lateral irons.
FLUOKIT M24+ – Operation Maintenance Instructions
Threaded fasteners with m4 Schneider Electric declines any responsibility for the following points: Other technical notices to be consulted.
The other brand names mentioned within this document, whether they be copyright or not, belong to their respective holders. The average water vapour pressure over a period of one month must not exceed 18 mbar. Pouring the cement top coat. Non respect of these instructions is likely to invalidate any guarantee. The interventions described are carried out on de-energized equipment in the course of being installed or fluoiit out non operational.
FLUOKIT M+ 24kV | Schneider Electric
It must be possible to enter or withdraw items of equipment without any handling difficulty. Passages must be designed to permit easy maintenance for all of the substation’s elements circuit breaker, transformer, etc.
Preparation of the sections Two profile sections must be laid out, one at the rear and one at the front, in the lengthwise direction of the switchboard. Fluokig the un-surfaced exposed concrete, pour a top coat of smooth finish, without ballast.
ECOFIT Fluokit M24/FP
Browse our resource section and find the most useful tools and documents for all our products Browse Energy and sustainability services First, envision an energy-efficient, cost-effective and sustainable enterprise.
This opening must have a section of about 40x40mm to allow for the passage of the 25mm2 cable. Respect the imposed distances see chapter 5. The switchboard must not be exposed to any solar radiation. Each profile section comprises, every mm, a fixing plate welded and drilled with 2 holes of Geometry of the cable trough.
Reserve opening at the extremity of each rail. Realign the passage on the front inner edge of the cable trough. They must be equipped with all the correct protective equipment required for the task being performed. The durations for completing the operations mentioned given in the maintenance tables are purely an indication and depend on on-site conditions.
Installation of the switchboard The positioning of the Functional Units is primordial for: Installation of the switchboard. Contacts Group Schneider Electric service centers are there for: Local requirements especially about safety and which are in accordance with the indications given in this document, must be observed.
Symbols and important safety informations.
The irons also serve in levelling the cement topcoat.